Number of views:
Copper core XLPE insulated PVC sheathed copper tape shielded control cable
Product serial number
It is suitable for connecting wires of control, monitoring circuits and protection circuits with rated voltage of 450/750V and below. It has the characteristics of high mechanical strength, excellent electrical performance and chemical corrosion resistance.
Implementation criteria:Enterprise standard (refer to GB9330/IEC60502)
Conductor material:Oxygen-free copper (copper content: 99.9%)
Number of cores:multicore
Insulation material:XLPE crosslinked polyethylene
Conductor maximum temperature:105 ℃
Color:Red, Yellow, Green, Blue, Black, Yellow and Green
Scan the QR code to read on your phone
|Model||Product name||Number of cable cores||Cross section（mm2）|
|KYJVP2||Copper core XLPE insulated PVC sheathed copper tape shielded control cable||4~61||0.75、1、1.5、2.5|
● Conductors: copper conductors, divided into 1 type of single conductor, 2 types of stranded conductors and 5 types of stranded conductors
● Insulation: XLPE crosslinked polyethylene
● rated voltage Uo/U:450/750 V
● The allowable long-term maximum working temperature of conductor is 90℃
● Short circuit maximum core temperature (duration not exceeding 5s): 250 C
● Operating temperature range: -20 to 90°C
● When laying, the ambient temperature shall not be lower than 0℃
● When laying, the bending radius shall not be less than 12 times of the outer diameter of the cable.
● Cables weighing less than 80kg are allowed to be delivered in loops. Each finished cable must be no less than 100m long or delivered by any length agreed by both parties.
● Allow delivery of any length according to the agreement
● The cable must be securely fastened during transportation to avoid damage to the cable or the disc caused by collision or overturning.
● Prevent serious bending and other mechanical damage to the cable tray.
● It is strictly forbidden to drop the cable tray with cables from the height during transportation.
● Cable hoisting uses special lifting equipment. It is strictly forbidden to lift the cable or directly drive the cable from high altitude.
● The length measurement error should not exceed ±0.5%
● The finished cable should be stored in an environment with a temperature between 0 and 40 ° C and a humidity of 85% or less. Do not expose it to direct sunlight or rain. Use proper ventilation to keep the environment dry.
● The coiled or formed cable should be wound up neatly and properly packaged. Cable reels shall comply with the provisions of JB/T 8137-1999.
● The cable end should be reliably sealed. The cable end protruding from the outside of the disk should be covered with a protective cover. The extension length is less than 300mm.
● The cable package should bear a label indicating:
a) Manufacturer's name and trademark
b) Cable type and specifications
c) rated voltage
d) length (m)
e) Weight (Kg)
f) date of manufacture
g) Standard number or certification mark
h) Symbol of the correct rotation direction of the cable reel
● When installing, the ambient temperature should not be lower than 0 °C. If the temperature of the thermometer test environment is lower than 0 °C, the cable should be pre-heat treated before being installed.
● The bending radius during cable laying should be strictly controlled to avoid mechanical damage inside the cable.
● If a quality accident occurs in the cable laying process (such as damage to the outer sheath), it should be repaired immediately or notified to the after-sales service department of the company.
- E-mail: firstname.lastname@example.org
- Chengtiantai Industrial Park, Jinjiao Industrial Zone, Lisonglang Community, Baoan District, Shenzhen
©2010-2019 Shenzhen Chengtiantai Cable Industrial Development Co.,Ltd. 粤ICP备05044349号